This historic book may have numerous typos and missing text. Purchasers can download a free scanned copy of the original book (without typos) from the publisher. Not indexed. Not illustrated. 1987 edition. Excerpt: ...to 80F (27C) by adding 0.004 for each 10F (-5.5C) that ambient temperature exceeds 80F (27C) or subtracting 0.004 for each 10F (-5.5C) that ambient temperature is below 80F (27C). (4) If, after correction, the specific gravity of any cell measures below 1.270, the battery should be charged. If any cell cannot be charged to a specific gravity of at least 1.270, the battery is not acceptable and should be replaced. MARINE CORPS TM 6115-12/7 AIR FORCE 10 35C2-3-471-1 NAVY AG-320BO-OMM-000 4-27. BATTERY. (cont) d. Installation. (cont) (5) Stow power cable on cable support. 4-28. WIRING HARNESS. See 1, FO-1 for location of wiring harness, Wl. Maintenance of the wiring harness (figure 4-15) connecting the generator to the GECM consists of inspection, test, replacement, and repair. a. Inspection. WARNING To prevent injury, ensure that battery is disconnected before performing maintenance on electrical components. (1) Disconnect battery cable plug connector from battery. (2) Loosen turnlock fasteners and remove engine housing access cover. (3) Open control panel access door. (4) Loosen turnlock fasteners and open control panel. (5) Inspect for loose connections on GECM and generator. Tighten loose connections. (6) Inspect for broken wires. Replace broken wires (paragraph 4-28d). (7) Inspect for damaged insulation. If insulation is damaged to extent that bare wire is exposed, replace wire (paragraph 4-28d). (8) Close control panel and secure with turnlock fasteners. (9) Close control panel access door. (10) Install engine housing access cover and secure with turnlock fasteners. (11) Connect battery cable plug connector to battery. b. Test. Testing consists of performing continuity checks on the wiring harness. All readings should show continuity and low...This historic book may have numerous typos and missing text. Purchasers can download a free scanned copy of the original book (without typos) from the publisher. Not indexed. Not illustrated. 1987 edition.
|Title||:||Operator's and Unit Maintenance Manual; Gas Turbine Engine Driven Aviation Generator Set, Nsn 6115-01-161-3992|
|Author||:||United States Dept of the Army|
|Publisher||:||Rarebooksclub.com - 2012-07-04|