TABLE 6 a Minimal cut sets for scenario 3, fire outside room, annual inspection, discharge test in 1977, no leakage test, ... D5 Control circuit failure C2, C3 System manually aborted, smoke continues to enter C4, C6 No manual activation upon detection, ...  U.S. Department of Energy, aquot;Standard for the Protection of DoE Electronic Computer/Data Processing Systems, ...  Abbott, J. L., aquot;Model A -1301 Series Total Flooding Fixed Extinguishing Systems Using Ansul 1301, aquot; Factoryanbsp;...
|Title||:||Fire Hazard and Fire Risk Assessment|
|Author||:||M. M. Hirschler|
|Publisher||:||ASTM International - 1992-01-01|