The correction factor is multiplied by the friction loss obtained from Figures 18-1 or 18-2 for each straight duct section. ... or have been computed, and c an be found in tables in the SMACNA aquot;HVAC Systemsa Duct Designaquot; manual. ... pressure loss for any duct element whose dynamic loss coefficient aquot;Caquot; is known, using the following equation: Equation 6-2 TP = C x Va Where: TP = Total pressure loss (in.
|Title||:||Environmental systems technology|
|Author||:||W. David Bevirt, National Environmental Balancing Bureau (U.S.)|