The transfonner room exhaust air temperature should not exceed the design limit of the transformers. ... an electric reactor room. lf the reactors have ducted connections for the exhausts, a removable section may be required so that the ducts can be disassembled ... The design should use NFPA Standards such as 37, 70, and 90A, insurance carrier requirements, and applicable local codes and standards.
|Title||:||ASHRAE Handbook. Heating, Ventilating, and Air-conditioning Applications|
|Author||:||American Society of Heating, Refrigerating and Air-Conditioning Engineers|
|Publisher||:||American Society of Heating Refrigerating and Air-Conditioning Engineers - 1991|